The burning in Trepca caused the interruption in Mitrovica
Today, around 12 o'clock, a trafo is being burned inside Trepca building, which is also at the ownership of this enterprise. At the same time the 110 kV line of KOSTT in Mitrovica was broken.
This has caused to have Mitrovica left without electricity.
KEDS has immediately sent the teams to the scene, where also the management from Pristina headed there to assist these enterprises to overcome this situation as soon as possible.
KEDS has managed to return electricity for around 2/3 two-thirds of Mitrovica's customers, bypassing the supply from the lines coming from Vushtrri, while there is no alternative for customers supplied by Trepca and the KOSTT line in Shupkofc, namely a part of Mitrovica and the villages near Mitrovica in the direction of Vushtrri.
Kompania Kosovare për Distribuim dhe Furnizim me Energji elektrike SH.A
Kosovo Electricity Distribution and Supply Company J.S.C
Kosovsko Preduzece za Distribuciju i Snabdevanje Elektricnom Energijom D.D